9-13 W.C Spring 1/2 x 1/2 NPT 9-13 W.C Spring 1/2 x 1/2 NPT Emerson Process Management Regulator Technologies Inc. Emerson-Fisher LP-Gas Equipment R622-BCF 2nd Stage Regulator
Emerson-Fisher LP-Gas Equipment R622-BCF 2nd Stage Regulator, 9-13' W.C Spring, 1/2' x 1/2' NPT: Industrial & Scientific. Emerson-Fisher LP-Gas Equipment R622-BCF 2nd Stage Regulator, 9-13" W.C Spring, 1/2" x 1/2" NPT: Industrial & Scientific. Body Sizes and End Connection Styles (inlet x outlet): 1/2-inch x 1/2-inch NPT . Maximum Inlet Pressure: 10 psig / 0,69 bar : Emergency Inlet Pressure: 50 psig / 3,4 bar . Outlet Pressure Ranges : 9 to 13-inches W.C / 22 to 32 mbar . Capacity : 875,000 BTU/hr . Vent Size : 3/4 NPT screened . R600 Series second-stage regulators are Underwriters Laboratories (UL) listed designed to reduce the Outlet pressure from a first-stage regulator in domestic LP-gas (propane) systems installations. Type R6 is designed for two-stage domestic applications up to ,00,000 BTU per hour/5, scmh. Type R6 contains a high performance Relief Valve and a large /-inch Screened vent to limit downstream pressure to less than PSIG/0, bar in an overpressure situation. Types R6 and R65 are designed in an angle body and back mounted design..!!! WARNING !!! Failure to follow these instructions or to properly install and maintain this equipment could result in an explosion and/or fire causing property damage and personal injury or death. Fisher equipment must be installed, operated and maintained in accordance with Federal, state and local codes and Fisher instructions. The installation in most States must also comply with NFPA no. 5 and 5 standards. Only Personnel trained in the proper procedures, codes, standards and regulations of the LP-gas industry should install and service this equipment. .BUYER AGREES THAT RESPONSIBILITY FOR PROPER SELECTION, INSTALLATION, USE AND MAINTENANCE OF ANY PRODUCT REMAINS SOLELY WITH THE PURCHASER AND END-USER. BUYER AGREES TO COMPLY WITH THE ABOVE WARNING AND ALL INSTRUCTION MANUALS, BULLETINS AND INSTALLATION GUIDES ASSOCIATED WITH THIS PRODUCT.. . . .